Repair of two SIHI hot oil pumps. The repairs included replacing all of the seals, gaskets, O-rings, shaft, mechanical seal assembly, thrust bearings and radial sleeve bearing. Great work by our repair team to say the least.
Dean hot water pump repaired and ready for return to the customer. The repair included replacing the mechanical seal assembly, shaft, gaskets, o-rings, gland, thrust and radial bearings. We covered the pump with a nice coat of high temperature black paint and shipped it out this morning.
Check out this gas skid that we pulled out of a Michigan automotive assembly plant. We completely tore down and refurbished the skid and it is now being installed at a Chicago automotive assembly plant. You can see by the original condition of skid that the biggest challenge was getting it to look new again […]
Gusher 7550 Series Vertical End Suction Centrifugal Pump with a 54″ extension repaired and heading back to the customer. The repair included motor replacement, bearings, seals, carbon mid-bushing, gaskets, cleaning and paint. These kind of pumps are great for a wide range of industrial applications like spray booths, industrial spray washers, paint and coolant systems.
This Griswold pump with 4×6-13 CD4 construction came to us with extremely low flow. To fix the problem, our repair team replaced the impeller, shaft sleeve, cartridge seal and administered a complete bearing frame repair that included bearings, oil seals and labyrinth seals.
This Gusher 7550 series vertical end suction pump was dropped off at our shop in bad condition. A bearing failed due to the shaft dropping and created a ton of wet end wear. We went ahead and repaired the pump with a wet end kit supplied by Gusher and replaced the motor, bearings and bearing frame. Looks […]